PolyPro® Polypropylene Vent Pipe
PolyPro and PVC/CPVC PVC pipes are commonly used for venting water heaters, condensing boilers and warm air furnaces, yet PVC was never designed for such use. An environmentally safe and engineered alternative is PolyPro, for condensing gas appliances. Engineered for venting, it is 100% recyclable, and contains no toxic or carcinogenic materials, chlorides, or heavy metals. PolyPro does not release hazardous gases during combustion, and has been used safely throughout Europe for over fifteen years. Polypropylene has a higher operating temperature limit of 230°F/110°C (PVC is 149°F/65°C max and CPVC is 194°F/90°C). PolyPro is engineered with a corrosion-free, condensation management system.
PolyPro is a polypropylene vent pipe for use with ANSI Category II and IV gas-burning appliances, including highefficiency water heaters, condensing boilers and warm air furnaces. Poly Pro is listed by Intertek to the ULC S636 standard in Canada as a Class IIA, IIB and IIC vent system suitable for exhaust temperatures up to 230°F / 110°C, and a maximum positive pressure of 15 in-w.c.
Materials and Construction
Rigid pipe constructed of 2.2mm (minimum) thick polypropylene. Flex is double-wall polypropylene. EPDM or Viton gaskets.
0" clearance to combustibles for exhaust temperatures up to 194°F / 90°C, and 0" clearance for vertical installations up to exhaust temperatures of 230°F / 110°C and ¼" / 6mm clearance to combustibles for horizontal installations at exhaust temperatures up to 230°F / 110°C . PolyPro concentric vent system components, including concentric Horizontal Termination and Vertical Termination, are listed at 0" clearance to combustibles for exhaust temperatures up to 230°F / 110°C.
2" (60mm), 3" (80mm), 4" (100mm), 5" (130mm), 6" (150mm), and 8" (200mm).
Listed with the appliance in the USA, check with appliance manufacturer. Intertek / ETL listed to ULC-S636 Listed as a Class IIA, IIB, and IIC vent system.
877 Cotting Ct.
Vacaville, CA 95688
Tel: (800) 835-4429
Fax: (707) 446-4740
Web site: http://www.duravent.com/Duravent.aspx