PolyPro® Flex Double-Wall Flex Lining System
PolyPro Flex through B Vent as a Chase. Retrofit venting for new, high-efficiency appliances When replacing a mid-efficiency appliance with a new condensing 90+ appliance, you can use the existing B vent (any brand) as a chase for the new appliance with PolyPro. The perfect solution for utilizing the B Vent already in place, just insert double-wall PolyPro Flex through the B Vent pipe, utilizing the convenient pull cone and terminate the system with PolyPros Skyline Vertical Termination Cap. At the other end is the unique B Vent/PolyPro Support Cap, allowing for the connection of flex to rigid PolyPro lengths and elbows to finish the installation.
PolyPro is a polypropylene vent pipe for use with ANSI Category II and IV gas-burning appliances, including highefficiency water heaters, condensing boilers and warm air furnaces. Poly Pro is listed by Intertek to the ULC S636 standard in Canada as a Class IIA, IIB and IIC vent system suitable for exhaust temperatures up to 230°F / 110°C, and a maximum positive pressure of 15 in-w.c.
Materials and Construction
Rigid pipe constructed of 2.2mm (minimum) thick polypropylene. Flex is double-wall polypropylene. EPDM or Viton gaskets.
0" clearance to combustibles for exhaust temperatures up to 194°F / 90°C, and 0" clearance for vertical installations up to exhaust temperatures of 230°F / 110°C and ¼" / 6mm clearance to combustibles for horizontal installations at exhaust temperatures up to 230°F / 110°C . PolyPro concentric vent system components, including concentric Horizontal Termination and Vertical Termination, are listed at 0" clearance to combustibles for exhaust temperatures up to 230°F / 110°C.
2" (60mm), 3" (80mm), 4" (100mm), 5" (130mm)
Listed with the appliance in the USA, check with appliance manufacturer. Intertek / ETL listed to ULC-S636 Listed as a Class IIA, IIB, and IIC vent system.
877 Cotting Ct.
Vacaville, CA 95688
Tel: (800) 835-4429
Fax: (707) 446-4740
Web site: http://www.duravent.com/Duravent.aspx